Carbon Monoxide & Smoke Detector Regulations
Carbon Monoxide Alarms - What You Need to Know
On April 7, 2003, New Jersey adopted regulations for the installation of Carbon Monoxide Alarms in the vicinity of all sleeping areas in buildings that contain fuel burning appliances or have an attached garage.
Carbon Monoxide Alarms should be installed with 10 feet of any sleeping areas so they will be audible in each bedroom. Multiple carbon monoxide alarms may be necessary to accomplish this requirement. The use of a combination smoke and carbon monoxide detector is allowed to fulfill the requirement.
Smoke Detectors - What You Need to Know
Smoke detector requirements vary because of code changes adopted over the past years. At a minimum, homes built prior to January 1977, require battery detectors to be installed. One on each level and outside of each sleeping area usually with 10 feet of any bedroom doors. The use of a combination smoke and carbon monoxide detector is allowed to fulfill the requirement.
- Any detector that is older than 10 years must be replaced under this requirement.
- As of January 1, 2019, 10-year sealed battery-powered alarms shall be installed in accordance with ANSI/UL 217.
- Any building constructed after January 1977 needs to meet the requirements of the code at the time the building was constructed. If the code only required hard wired smoke detectors on one or two floors, hardwired detectors need to be installed on each floor. However, A/C-powered single or multiple-station smoke alarms installed as part of the original construction or rehabilitation project shall not be replaced with battery-powered smoke alarms.
- All battery-operated smoke detectors that use removable batteries must be replaced with the sealed battery requirement mentioned above
- All installed systems must be maintained at all times (IFC 907.1.11.2)
Low Voltage Fire Alarm Systems - What You Need to Know
All low voltage fire alarm systems and fire alarms that are monitored by a central notification station must be maintained in accordance with NFPA 72 and the homeowner must provide a system test report at the time of inspection. Failure to provide a system test report that shows no deficiencies will be cause for failure and a re-inspection will be needed.
Starting January 1, 2006, Mahwah Fire Prevention will begin enforcing the adopted state requirements (N.J.S.A. 52:27D-198.1) for fire extinguishers in one and two family dwellings along with smoke detectors and carbon monoxide detectors at the change of occupancy.
The requirements for extinguisher type and placement are as follows (N.J.A.C 5:70-4.19(e):
- At least one portable fire extinguisher shall be installed in all one and two family dwellings upon change of occupancy.
- The extinguisher shall be listed, labeled, charged and operable.
- The size shall be no smaller than 2A:10B:C, rated for residential use and weighs no more than 10 lbs.
- The hangers or brackets supplied by the manufacturer must be used.
- The extinguisher must be within 10 feet of the kitchen and located in the path of egress.
- The top of the extinguisher must be no more than 5 feet above the floor.
- The extinguisher must be readily accessible location and not obstructed from view.
- The owner's manual or written information regarding the operation shall be provided during the inspection
- The extinguisher shall be serviced and tagged within the past 12 months or the seller must have a receipt for a recently purchased extinguisher.